Hope you are doing fine
F.22 error means Dry fire. Too little water in the appliance, water pressure sensor defective, cable to pump or water sensor defective, pump blocked or defective, pump output too low...you need more water in the boiler
This error is usually caused due to low pressure
There are two taps underneath...you have to open the left one first and then the right one....the tap on the left allows water to come from the mains up to the boiler the one on the right allows the water to enter the boiler
Turn both of them on, let it fill up for not for long but make sure that it rises to 2 before you close them
It should start working straight away...let me know how it goes...I'll wait
Is it working ?
I can see you have stepped out of this chat....please let me know if you need any more help and if that worked
sorry I have just received half of the message that you have sent
have you received my message ?
Please check this Video .... it tell you what to do...let me know if you still need any assistance, I am willing to help you
The video was sent just to give you an idea of what has to be done :)...basically that is the only way to increase the pressure...let me know if you have already tried with those side pipes ?
Ok just here with my fellow experts...you are right Ecotec comes in two models: Ecotec pro and Ecotec Plus...On the plus model the filling loop is directly under the boiler. The filling loop should be disconnected after use, so you might need to re connect one end. Increase the pressure to just over 1 bar when the system is cold. If the problem is still there after doing all this then check it for possible leaks...let me know if you need more help..
OK...you can get back to me if you need any assistance and I will help with no additional charges....Excellent feedback is appreciated if you are satisfied with my assistance :) Please don't rate the solution till the time you are completely satisfied...Thanks