Had an engineer come out to fix my Potterton boiler as it had a E133 code flashing: no hot water, no heat. I told him it was a fault with the gas supply per the booklet. He ignored me and replaced the PCB board and other parts in the boiler. Still no joy. He left and I called British Gas who sent out National grid who came out and replaced the hose on the gas meter as it had failed. The boiler now works to give hot water, but won't always work to give heat. Sometimes it does, sometimes it doesn't. The colder it gets the less it comes on and last two (cold) days won't come on at all no matter how much I reset it off the control panel. It seems the signal from the thermostat isn't kicking in to turn on the heating. I read to push the TRIP button but I don't know what that looks like or what to do exactly. I want to try that and see if the problem resolves before calling out another engineer. I have a Promax Combi HE Plus
Do you have the model of your room thermostat? Please
T4RF Wireless system, UT2 Single channel timeswitch,
thermostat shows sending signal. light green on sensor by boiler, not flashing though
Hi . I think what happened was that when the British gas guy turned off the power , your thermostat lost contact with the recieved box . there is a process to reconnect the two . if you give me a minute I will try to find them instruction , thanks
Ok . does your recieved look like the box on the right in this photo?
yes, I have both of these
light is green on box on the right,
no red light flashing though
but mine is WR1 British Gas (looks exactly the same)
Yes,they are the same.. Ok would you like to go through the reconnection process?. I may be a bit slow as I am switching back and forth between web pages
According to the info I have, if I pull out the battery on the thermostat, hold the set button, it is supposed to show rF. Mine stays blank until I release and then it is just the normal display of the temp and sending signal. Heating comes on once a day, won't come on on-demand, and won't come on on set times. It comes on for the first time set but not the other two.
take your time. I'm just telling you what I have tried. Thanks
Ok. I have a little different
red light doesn't flash. Green light is supposed to flash every 4 seconds or something like that. Doesn't flash at all ever. The red light will flash when turned off at the mains and when override/learn buttons are pushed. Then just solid green. I hate this wireless thing. It's never warm enough in my house (just saying). Now, I'll stop and wait for you. Sorry
Turn power off to reciever. Pull out batteries on room stat transmitter
Leave off for at least 5seconds
ok have turned off electricity to WR1 and pulled out batteries from thermostat
Leaving room stat off , turn power to receiver back on , there should be a red light on the reciever box.
Ok . to check the reciever is wired up right press the override button once.the boiler should fire and come on
nothing happens. if I press learn/override green button comes on, red is solid red, not flashing, boiler doesn't spark (but I never noticed in 6 years it did that)
boiler is downstairs and I am fat and old so takes me awhile to go up and down from boiler to computer, sorry
Ok . the boiler should come on . is the programmer on for heating? If not put it on and repeat the process . I don't mind waiting , I'm in all day today
Yes, it's on for heating. I have this same stupid problem every year convincing it to start up, but I've never had it where it only comes on when it wants and not when it's programmed. Once I get it going (last 5 years) it will come on when I set it to steady on. I'll go down and try this all again to be sure I have done it in the right sequence. Two minutes...
Hi . just reread what you wrote . are you saying that tyhecheating does come on once? A day
ok. when I turned it off at the wall and turned it back on the boiler fires. pressing the override doesn't do anything. my husband said it was on early this morning and the radiators were hot. it probably was as it seems to come on on the first setting at 4:30 am. Problem is once it goes off, it stays off and won't come back on for the other two timinigs. Also, I don't think it is coming on at 4:30am unless I've done all this reset stuff at bedtime. I have set the timer to be on for 24 hours when it comes on at 4:30 am. Husband said radiators were hot this morning but they are cold now and it won't come on at all. So I think when I reset it, it is convinced to come on once, to a certain point, then stops and does nothing. I reset it, it comes on at 4:30am only. Not when I reset it.
by the way, the battery case is till out of the thermostat. I think the guy who replaced the pcb either gave me a dodgy board (was supposed to be new) or didn't wire it up right
Hi .can you try to hold down button 1, keep depressed , then hold down button 2 keeping it depressed.the red light should flash a couple of times and then go out. The lights should be on .then put batteries back into the room stat( if you can take it to the reciever that would be better) . the reciever should flash seven times , this confirms the two are linked
Ok I understand what you are saying and I have tried this repeatedly. The red light won't flash even though the thermostat shows sending a signal. And the green light is supposed to flash every 4 seconds or so and it isn't flashing at all (have this problem every year, not this bad though). I'll go down now and try what you said. I can't take the room stat to the receiver unless I unscrew it. Should I do that? Just unscrew it to remove it from the wall and carry it in? I have tools and I know how to use them. Waiting if you want me to remove thermostat from wall before I go down.
Yes just unscrew it
ok here I go
ok. red light flashed repeatedly, green light came on, red light went off, green light on solid green. boiler not coming on
the green light is supposed to flash every so often after restart and it isn't flashing like that, just stays soild green
Ok . so your heating is on at the programmer , on at vthe room stat ? But not firing boiler?
Ok . we can wire the reciever wiring to bypass the room thermostat, to give heating . this will confirm the boiler is working ok . do you think you or your husband would feel ok to do this?
I can do anything like this as long as I don't electrocute myself
No , safe working is essential . turning off the power whilst rewiring.
I am sure the boiler is ok. I wonder if the pcb wasn't connected right when the guy installed it as it does work sometimes.
I think the fault may lie with the wireless room stat and or reciever. If we wire these out and bypass them this will confirm that the boiler is working ok for heating
i would like to bypass the room thermostat though. i hate that stupid thing. i just want heat to come on when the timer is on and when i set it to constant on.
so this would be good. is it very difficult though?
You would need a flat head srewdriver
got it, got several, got lots of tools
im putting this on my mobile now so i can read it as i'm doing it downstairs
Ok . turn power off to the heating system , vpconfirm all the lights are off , then remove the front panel off cthe reciever
Should be a small screw somewhere, maybe underneath
That's ok , take your time
Him. It may not be a screw but clips that need pressing in
Ok .so you can see the wires?is there a connector block? And are the connections labeled , is numbers or letters or both?
Ok. Give me a couple of mins , please
Do you have a brown wire in what connection and a blue in what connection?
Ok. Remember where the original wiring is . take a photo or write this down . then take out wire from c and put it in to call
Hi , sorry can you give me2 mins?
Yes , sorry that's right. Grey into same as black in 3
That's ok . sometimes it helps to push on the srcew as you turn it
Yes, it will keep it safe there if needed later
Ok . once the screw is in ,tighten , replace reciever cover , turn on the power and the heating should come on .if it doesn't come back to me .
Hi , Will be offline for a couple of hours , back vasap
working great. thanks for your help
Your welcome , but you did the work , well done
Hi . would you mind rating me , thanks.
I want to give you extra pay for working with me because it took so long. can I do the extra help for £15 by phone, but we don't need to talk. You deserve extra and I want to pay you extra.
and yes I will rate you excellent don't worry
That's ok , you were great , all the best , Toby
ok. many thanks. you were great. I just did what you told me. have a great night. (wish you'd take the extra pay though. you saved me a bundle helping me do it myself)
Hi . don't worry , I have never known a boiler to blow up . you are very safe as they have too many safety features to never allow that to happen.reset won't make any difference . it may be that now you have totally focused on the sound your boiler makes, it seems loud but is probably just the pump and fan . if you want it warmer turn the boiler stat to max...can you let me know if you got this last , thanks
If you are really worried , get another boiler engineer who has been recommended by family, friends who they have used more than once