Hi . can you confirm the boiler pressure , please
Ok thanks. 02 is flame detected with boiler off . this will be either a faulty flame detection probe or a faulty board.
What is 02
Hopefully it will be the probe as the board is expensive
Was it not 02 ,sorry got a lot happening here . ok let me check for 03. Thanks
Ok . high limit overheat stat has operated. This will be down to a faulty thermistor/temperature stat . or your pump has failed .
Thanks. Shall I change the temp stay then?
I would check the pump is spinning first . there is a bleed screw on the middle of the face of the pump . if you undo this ( a bit of water will release , get a towel ) and reset the boiler , insert a Phillips screw driver into it and see if you can feel the motor spinning , also , if you can see if you can stop the motor by pressing lightly. If you can stop it then replace the pump . if the pump seems ok , then replace the heating stat .
Ok will do
Thanks for the advice.
Would you mind rating me , thanks
o i take the bleed screw all way out?
Some pumps will drip , some will squirt
I have noticed that the letters FI on display which means purge but it stays purging for 2 mins the shuts iff
Ok ,purge is normally purgining the gas line
Do up you mean f1 or f11?
Does the boiler go to fault on hot water and heating?
Is it a new installation?
Hi , do you still require help?