Hi . are you wiring in a room stat?
In the boiler wiring centre there will be a 240v switched lived connection. There will also be low voltage or volt free inputs. Don't use those
Have you got the boiler model or GC and I will check the wiring diagram,
Ok , give me a minute, thanks
Page 27, 230v section .remove the link in 3 and 4 and put switched lie in 4. If 4 didn't work it will be 3.
No the bus is for specialised ebus controllers, usually weather compensation units etc
No . the motorised valves etc work off 240/ 230volts , so the power from the switched live will be the same . if you put it in the low voltage or bus you may damage the boiler pcb
If there is a link in 3 and 4 in the 230volt section you can remove it and put switched live in 4
Hi . if happy with your answer , would you mind rating it , thanks
Hi , could you please rate your answer , thanks