, can you ear the fan start up?
Also what pressure do you have
Is no fan that I know of. I have no guage, but message F.75
Ok , give me a few minutes please to check that code , thanks
, what pressure reading do you have?
I have no guage, but message F.75
The message is low water pressure/ faulty pump/ faulty flow switch.
You should have a gauge on the boiler control panel
If not then it will be on the digital display
Press the I button , should be a reading in bar
Sorry guage is on RH side and hard to see. It reads just above red, in the black.
Pressing i causes no change to the display.
I have tried turning the taps. Causes a rushing sound inside, but still will not light
Ok .you will have to fill tgevappli
Fill the boiler until half in the grey/ black
Pressure now well above red, in middle of grey
Ok, did you fill it up?
If you did.turn the boiler power off and back on to reset.
Presumably. I now have a drip every two seconds from the boiler, so maybe that's myn problem Although it only happened after I turned taps on then off
Appears you have a leak . this must have dropped the pressure stopping the boiler from working, . do you want to try and locate your leak.
Is your boiler still leaking?. Do you think this was from the filling mechanism or another component?
It seems the leak only occurred when the tap was open, so it's prob not too urgent. I'll the engineer when he coimes to service.
Meanwhile since resetting I have both hot water and CH it seems.
Pressure is healthy, digital reading reading is 38C & climbing
Ok. Has the dripping stopped?
Yes it has. I think we can close this dialogue soon
If still dripping the pressure will drop again and the boiler may stop working
Ok , that's great .
Not dripping. If I get the same problem in next few days I'll call my friendly engineer
Would you mind rating your answers , thanks
Just about to .....