Hi Ian..........I presumed I was involved with a Ferroli Tempra 24 gas boiler Gas Safe registered engineer familiar with boiler troubleshooting....as a home appliance engineer I'm not sure you're the right person ???
That is fine, I will happily opt out if you wish to speak to someone else ~ kindly note that I am also a HVAC engineer but not specific to Ferroli. Have a great day and good luck with your question.
Hi again Ian.......I really need to connect to a Ferrolli gas boiler engineer who has much experience with the Tempra 24 troubleshooting/diagnostic fault finding where I as an installer have limitations in this area. I am obviously reluctant to part with £27 unless I liase with the right man.
Hi. If the boiler has fired this proves the fan , air pressure switch . it will most likely be the flow thermostat or the flame recognition probe , but as you are not getting a fault code it will most likely be the flow thermostat .if its a thermistor this can be tested on ohms with a multimeter, it will be within a certain range at a certain temp . but you should get a change with temp change. I have worked for British gas as a boiler breakdown engineer , plus others
Thanks for your response.......I'm checking things out this afternoon and will speak to you later.