Hi , you
Hi . I will run through the fault with you
is anyone there
Hi , from the info you have given it is your domestic heat exchanger that has blocked up with sludge or scale
When this happens the water can't move through it quickly enough , there for it overheats, burner cuts out,goes cold restarts and continues like that. Change the domestic heat exchanger and it will be fine . please be sure to rate my answer , thanks
Why the have you rated me bad service . I have just told you what is wrong . can you please have the decency to explain
H, now for some reason I am able to connected to you
Hi, sorry about the rating before but every time I tried to view the answer it would just ask for a rating and your answer wasn't visible.
Ok . have you seen the answer I gave?
If you have recieved the answer and you are happy with it would you mind re rating, please. But if you need further info then we can continue until you are happy . please be aware I am not online constantly but check every 20 mins or so , thanks .