Hi Peter, It rather comes down to the rating of the appliances, for example if they are all 13A that takes to you 39A and you may get nuisance trips, you also have to take into account the cable run, you then need to factor in how likely it is to have all appliances running at full load at the same time.
From experience single ovens are around 13A, combi oven microwaves around 15A, and ceramic hob 30A, in this scenario your looking at 62A load, and this is far beyond the tolerance of a 6mm T&E and 32A MCB, but what load would you expect to pull (I cant see you having the two oven and hob on full power at the same time).
I would run a second 6mm from the consumer unit with its own MCB, and probably connect it to the ceramic hob if this load is around 30A.
Hi, I havent heard back from you, if you have everything you need, please rate the service received using the star rating, so I can close the case.
Should you need any further assistance please advise how I can assist you further.
Hi Peter, I havent heard back from you, if you have everything you need, please rate the service received using the star rating, so I can close the case.