Plumbing Questions? Ask a Plumber for Answers ASAP
It seems the professional has left this conversation. This happens occasionally, and it's usually because the professional thinks that someone else might be a better match for your question. I've been working hard to find a new professional to assist you with your question, but sometimes finding the right professional can take a little longer than expected.
I wonder whether you're OK with continuing to wait for an answer. If you are, please let me know and I will continue my search. If not, feel free to let me know and I will cancel this question for you.
Thanks for your patience,
Thanks for replying.
We will continue to look for a Professional to assist you.
If you decide on a refund, or wish to keep the credit for a future question, then of course we'd honour it.
Thank you for your patience,
Please understand it is rare for us not to be able to find the right Professional to assist our customers. We can close this question and return your good faith deposit to the original funding source on request.
Please let me know how you wish to proceed and again I apologize for any inconvenience this may have caused.
I hope you will give JustAnswer a try again in the future,
I'll keep this open till monday for you and then if no reply, I'll refund you asap.
Sorry I won’t be around for a couple of days, thanks for the advice.
I see what you mean the CN9 connector houses the flue stat, cab stat, flow stat, water pressure stat plus a thermal fuse. I can make a link from sleeving and wire to join terminals together, but which ones to join, I’ve only got a schematic diagram.
Two questions: how do I know that the pump is running at full speed apart from the visual representation telling me the boiler is at max?
Why is there no alarm present when both CH and HW are running together or when the modulation drops from maximum?