Plumbing Questions? Ask a Plumber for Answers ASAP
Hi , when you say heat , is it heat as though when the boiler is normally on or could it be residual heat from the boiler. I think it may be thge pump overun thermostat fault . if its not that it will be the control box .
do you have an electrical test Meter?
Ok. I will check boiler at first.
I checked the boiler thermostat moving the temperature up and down and boiler start when move up and stop when I move down. I presume it s working ok.
Where it is located?how can I check if it work or not?can be fixed or have to be changed.
Hi. I can't find that pump over run thermostat. I checked around the boiler and pump but nothing.
Yes the one on the link you sent me
I founded but what you mean with power at the switched live?brown from thermostat it's coupled together with brown from pump In the main switcher.
I got it👍
Ok. I will.
Hi. I checked t2 with the programmer off and there is live.
can be the programmer fault?
2 one for hot water and one for radiators
I took off the face of the programer and life still on the t2
I am out now. I will be back on this Monday. Have a good weekend. 👍
Hi. It's 5 and 6 the panel wired For hw and heating
Panel control off. Motorised valves are closed. There is live in orange wires 2 of them.
No. Levers are strong. I pushed them to check and they are going back in the closed position.
In the panel control it is 3 and 4 for hw and heat. Not 5 and 6. Sorry
No power on t2 after I took orange wires off.
hot water was live. 🎉
Yes just the head. Just the motor will be ok ?
I checked the valve it is working ok. I turn with my hand.
Thank you very much for your help. I will keep watching the boiler for next days to be sure all ok. If I have any problems can I contact you?
Hi. I have now live in both orange wires from valves. Boiler it s still running.
I took off the face and still live in wires.
What you mean?
I took of just the orange wires. All else stay the same