Plumbing Questions? Ask a Plumber for Answers ASAP
Hi , wire the receiver unit into the boiler wiring centre. Take the permanent live,neutral and earth(if required) from there and into connection terminals in the reciever. You will need is(live send) and or(live return) for the switching of the altech receiver.
Hi, yes take 6he ch link wire out,leave hw in. Use live from link into thermostat common and out of receiver i to ch. If you need neutral take it from the far right
OK do you have a multimeter - lets try and stay on this question text and I will sort the other questions out in a moment.
OK - power off.
Orange Connector on boiler - remove both wires from the L terminal
a. Remove link wire from Central Heating (CH) from yellow terminal.
b. Connect link from HW back into Orange L together with Brown wire that you have stripped back. This is you live feed to the thermostat.
c. Connect the stripped blue cable to the Yellow CH terminal.
Assuming that you have feed the Brown to the live at the thermostat and the Blue is the switched live return from the thermostat you are now correctly connected - Would you now kindly rate the information given by selecting from the star rating system at the top of the page, once done further questions are free of charge. Thanks for using JA - Ian