Appliance Repair Questions? Ask a Technician for Answers ASAP
Hello. You have a faulty motorised valve . it is opening enough to let the hot water pass but is not making the switch to fire the boiler and pump. As they get weak they start to not pull all the way across and fail to close the switch as it should , replace the motorised valve and all be good .